We no longer stock this product, but can recommend Firetherm Intucompound as a great alternative.
Nullifire FR270 High Strength Structural Compound is a single part gypsum-based compound providing up to 4 hours fire resistance. Nullifire FR270 has been fire resistance tested in accordance with EN 1366-3, ETAG 026 and Classification 13501:2.
Usage & Purpose
FR270 High Strength Structural Compound is used to stop the spread of smoke and fire along services that pass through compartment walls and floors, whilst providing an unsupported load bearing capacity. The system also provides thermal, acoustic and air sealing performance. FR270 is suitable for the following service penetrations; single and bunched cables, cable trays, cable ladders, trunking, steel and copper pipes, unsupported multiple ducting/ damper penetrations, PVC and uPVC pipes.
Typical areas of use include health and leisure facilities, schools, universities, commercial. retail and industrial buildings.
For spans greater than 1800 mm or seals that require a UDL in excess of 2.5 kN/ m², please contact Technical Team for support.
Features & Benefits
- Fire resistance tested in accordance with EN 1366-3, ETAG 026 and Classification 13501:2
- Suitable for rigid and flexible walls
- Acoustics up to 50 dB
- Rapid setting, zero shrinkage formulation - can be used as pourable or trowel grade
- Minimum 25 years working life as per ETAG 026
IMPORTANT FIRE PRODUCTS NOTICE: The information displayed on this website should be used as a guide ONLY and our Technical Department should be contacted to obtain a tailored specification and any advice necessary before you place an order for fire protection products. Fire protection products are non-returnable except in accordance with Condition 8 of the Terms and Conditions and should be applied only by an individual with the necessary expertise and experience. We will not be held liable for any resulting damage to property, human life or monetary costs incurred due to the incorrect specification you have prepared or use of fire protection products caused by your negligence, including your failure to have contacted us to obtain the relevant advice/specification.
Be the first to ask a question about this product!