An extensive range of accessories and ancillary products for use with Nullifire (Firetherm) systems, helping the installation and application of firestopping products. Refer below to see the full range. To qualify for Express (1-3 day) shipping, basket value must exceed £75.00 + VAT. Orders below this amount will only be available on Economy...
We no longer stock this product, but can recommend Nullifire FP100 Intuputty Pads as a great alternative.
|Single||70 x 60 x 4 mm||Black/Silver||1567 kg/m3|
|Double||130 x 60 x 4 mm|
Firetherm Electro Pads provides fire protection within metal electrical socket boxes in fire compartment walls, simply sticking into (using Firetherm Intumastic) position at the rear of the socket box for up to 2 hours of fire protection. In the event of a fire, the intumescent graphite-based pads will expand to seal gaps, restricting the spread of smoke and fire through socket boxes.
Use Firetherm Electro Pads within GIB partitions, timber or steel stud construction, in power and light sockets within compartment walls.
- Up to 2 hours of fire protection
- Acoustic sealing
- Choice of installation methods
- Simple to install
- Suitable for most drywall applications
1 x Electropad = up to 120 minutes integrity and insulation (limited by wall construction).
Typically adhered into position using Firetherm Intumastic to the rear of Electropad.
Tested at Exova BM Trada to BS EN 1366-3 and BS 476 Pt 22
IMPORTANT FIRE PRODUCTS NOTICE: The information displayed on this website should be used as a guide ONLY and our Technical Department should be contacted to obtain a tailored specification and any advice necessary before you place an order for fire protection products. Fire protection products are non-returnable except in accordance with Condition 8 of the Terms and Conditions and should be applied only by an individual with the necessary expertise and experience. We will not be held liable for any resulting damage to property, human life or monetary costs incurred due to the incorrect specification you have prepared or use of fire protection products caused by your negligence, including your failure to have contacted us to obtain the relevant advice/specification.
Be the first to ask a question about this product!