Sherwin-Williams Firetex FX1003
Sherwin-Williams Firetex FX1003 is a single pack, thin film intumescent coating, designed for site application by airless spray, to provide ﬁre resistance for up to 120 minutes on structural steel.
**Available for delivery - see Delivery Options below**
After appropriate drying, Firetex FX1003 speciﬁcations can be exposed to the weather for up to 6 months provided that the speciﬁc use does not lead to ponding water due to rainfall, condensation or other site circumstances.
Sherwin-Williams Firetex FX1003 can resist normal weather conditions for up to 6 months without topcoat provided it has had appropriate drying prior to exposure. Once an approved topcoat has been applied as appropriate to the prevailing conditions, then durability will be substantially enhanced. If the speciﬁc use or storage could lead to prolonged contact with water due to rainfall, condensation, or other site/transportation/storage circumstances, then a recommended topcoat must be used to prevent damage to the basecoat.
Please note that this product should not be used without first receiving an application schedule from our Technical Department. Please download and complete the 'FIRETEX Intumescent Support Request Form' and return by email to [email protected]
If you have any questions regarding this process consult our technical department on 0113 2455450 (option 2).
Certiﬁre Approved – Certiﬁcate CF5077
This product has been assessed in accordance with the Criteria of Acceptability given in the ASFP/BCF “Industry Guidance Document”. This product has been tested and assessed in accordance with the ASFP ﬁ retesting protocol for cellular beam protection. See Section 6.3 from ASFP “Yellow Book” 4th Edition.
Several primers have been approved for use under Sherwin-Williams Firetex FX1003. For more information please consult our technical team.
For certain dry, internal situations where the ﬁnal colour/ appearance is not critical, then Firetex FX1003 may remain un-topcoated.
For externally exposed steelwork up to C4 and severe internal environments Acrolon C137V2 or Acrolon C237 must be used as a topcoat.
For other internal environments where a topcoat is required then Firetex M71V2 or Sher-Cryl M770 should be used. In all instances for subsequent re-decoration, use Firetex M71V2, Sher-Cryl M770, Acrolon C137V2 or Acrolon C237 as appropriate.
IMPORTANT FIRE PRODUCTS NOTICE: The information displayed on this website should be used as a guide ONLY and our Technical Department should be contacted to obtain a tailored specification and any advice necessary before you place an order for fire protection products. Fire protection products are non-returnable except in accordance with Condition 8 of the Terms and Conditions. We will not be held liable for any resulting damage to property, human life or monetary costs incurred due to the incorrect specification you have prepared or use of fire protection products caused by your negligence, including your failure to have contacted us to obtain the relevant advice/specification.
|andrew melvin on 2020-12-09 15:52:47|| |
what is the m2 cover on the firetex fx1003 per litre
There is no coverage rate per m² for this product.
The Intumescent must be applied at the specified WFT.
If you require assistance with a specification please contact our Technical Team on 0113 2545450 option 2.
|natalie on 2019-09-02 10:58:37|| |
Can I spray an eggshell paint over the FX1003 as a internal decorative ceiling colour in an industrial unit where only smoke detection is required and no sprinklers? Thanks
Sherwin-Williams Firetex FX1003 should only be over coated with an approved Sherwin-Williams topcoat. Assuming an internal C1/C2 environment, as an example Sherwin-Williams Firetex M71V2 could be used over Sherwin-Williams Firetex FX1003 and provides a decorative sheen finish topcoat in almost any RAL or BS colour.
|Clive Rowe on 2019-07-17 11:54:58|| |
What are the coverages recommended to attain 30 minutes fire rating on structural steel for FX1003?
In order to answer this question we would need you to provide our technical team ([email protected]) with as much of the following information as possible;
Alternatively you can just forward us drawings, fabrication/cutting lists and we'll extract the information from them but in that instance we'd need some guidance as to what to allow for i.e. all steels on first floor, etc.
|eric french on 2019-01-21 11:08:58|| |
what are the appropriate thinners/cleaner for FX1003 and C137V2 ?